On August 27 at the farmer enterprise "Shans" which is in Pervomaisk, there took place expeditious check of a condition of labor protection on the ammoniac refrigeration unit.
The press - the center of the Gosgorpromnadzor reports that check was caused by emissions of ammonia in premises of compressor shop that could become the reason of accidents.
During check it is revealed that in an engine room indicators of a source and signaling devices of emergency concentration of ammonia in room air aren't installed. Ammoniac pipelines and the heatexchange equipment didn't undergo periodic testing for durability pressure. Besides, an inspection of serviceability of safety valves on duty on devices (vessels) of the refrigeration unit isn't carried out. Serviceability of automatic devices of protection of compressors of the refrigeration unit isn't checked. On the condenser the manometer isn't installed. Besides, the enterprise didn't get permission of the Gosgorpromnadzor.
At present at the enterprise works on replacement of ammoniac installation on the freon are conducted.