From January 13 to January 22, 2009 the territorial administration of the Gosgorpromnadzor on the Nikolaev area carried out check of the enterprises which are engaged in storage and transportation of oil products. In total 5 enterprises from which 2 didn't get permission to performance of work of the increased danger were checked. 2 workers and 2 first heads were brought to administrative responsibility, reports a press - Gosgorpromnadzor service on the Nikolaev area.
When checking JSC Ukrnafta Nikolayevskogo gas Station of office and office in the Novoodesky area it was revealed that the opening for measurement of level of oil product in the tank has no metal ring that excludes an iskrosozdaniye. Also the faulty electrical wiring of devices of remote measurement of level of fuel isn't dismantled from приямков tanks, and at some gas stations tanks with gasoline aren't equipped with a gas binding.
On four gas stations a place covering fuel plum from a tanker needs under repair. At the enterprises the list of gas dangerous works which are carried out with registration of the admission of a dress and which are carried out without registration of the admission of a dress isn't developed. Besides, plans of an accident elimination for gas station aren't agreed with territorial bodies of the Ministry of Emergency Situations.
For example, during check JSC Oktan-N located in page. The resident of Ulyanovsk of the Nikolaev area, it was revealed that on the tanks specifying pressure of gas in interwall space, manometers aren't installed. The opening for measurement of level of oil product in the tank has no ring from metal which excludes an iskrosozdaniye and not the localization and accident elimination revised plan at gas station.
A number of violations was found at inspection of oil depots "JSC Bagor-Service and JSC Bogrom Oil. Besides, that the enterprises have no permission to performance of work of the increased danger, not all workers passed study and examination on labor protection.Annual measurements of resistance of grounding devices of this oil depot and obvalovaniye of reservoir parks aren't carried out. Besides, JSC Bogrom Oil didn't conduct periodic examination of tanks. During carrying out gas dangerous works on cleaning of tanks the dress admission isn't made out. Survey ditch for an autotranstime