Results of an investigation of case of poisoning of mother and the child inbecame knownNikolaev.
On March 25 in one of the Nikolaev apartments found dead the woman and her two-year-old child without signs of violent death.
Inspectors of management of the Gosgipromnadzor made investigation and found out that poisoning with gas became a cause of death of a family. The matter is that in the apartment the geyser and an extract over a plate at the same time worked, from - for it the draft direction changed, and carbon monoxide got to the room. Besides, from - for foreign interventions in the mechanism of a geyser the safety system didn't work.
As reports the Gosgipromnadzor, the identical situation directly in the apartment during the investigation was simulated. The special equipment showed that at plate and extract inclusion at the same time in kitchen carbon monoxide in the overestimated quantity concentrated.
- Safety rules of systems of gas supply of Ukraine forbid the device of exhaust ventilation with artificial motivation in the houses equipped with gas devices with branch of products of combustion in flues, - the deputy chief of territorial administration of the Gosgipromnadzor in the Nikolaev area G. Zhukov speaks. - One more factor which leads to similar cases, shortcomings of "Nikolayevgaz" work are. Many employees of this enterprise pokvartirno check indicators of counters, and it would be expedient to pay attention and to a condition of the gas equipment in the same time.
Since the beginning of year from - for poisonings with carbon monoxide in the Nikolaev area four persons were lost. The main reason for accidents - unauthorized establishment or intervention in operation of gas devices.