Results of investigation of death of the employee of the Nikolaev branch of "Ukrtelecom" became known.
As we reported earlier, on July 3 the electrician, the employee of branch of this enterprise in Bratsk the area, ended the work earlier and helped colleagues to remove the from a support a cable. When it took up a cable, the man hit with current. From traumatized he died.
This accident was investigated by the special commission of territorial administration of the Gosgorpromnadzor in the Nikolaev area.
As reports a press - control center, violation of safety requirements became a cause of death of the electrician.
Having considered operation of the equipment, specialists of management established that when checking the feeding line the sequence of operations was broken. At the beginning of work the switch it was put in the situation "Measurement", but in a course button switching on the measurement block that gave the chance of short-term existence of tension on a feeder is made. It also struck the victim.
Besides, works on feeding lines were carried out without use of figurative grounding.
As a result of the revealed violations which led to death of the person, three employees of the enterprise, one of which - the official are made responsible.
For prevention further similar accidents at the enterprise extraordinary training and examination on labor protection of the workers occupied on robots with increased danger will be provided, and also extraordinary instructing for all employees is carried out.