"Crime. Is NOT PRESENT"wrote about that On June 15 complex check began "Nikolayevoblenergo" OKP. As it became known, during complex check of JSC Nikolayevoblenergo by inspectors of territorial administration of the Gospromnadzor on the Nikolaev area 10 branches of the enterprise were checked.
352 violations are revealed and is suspended work of 59 objects of the increased danger. From - for revealed shortcomings 15 people are attracted to administrative responsibility, 12 of which officials.
The most widespread violations for the majority of branches is the lowered level of oil in power transformers. There are cases of course of tanks of power transformers and subcurrent in radiator junctions with the transformer.
Cases of use of the equipment which already fulfilled the term meet, or is used in failure condition. Metal designs and parts of switching devices need protection against corrosion. Besides, not all cable channels are closed by plates.
The enterprise annually doesn't carry out an inspection by means of geodetic instruments of situation of the main designs of production buildings in territories which give in to continuous vibration.
Besides, employees of the enterprise only for 25% are provided with individual means of protection of respiratory bodies.